for Philadelphia, PA
Great service-explained everything clearly
Arlene - Philadelphia, PA
I was more than pleased with the service and the manner of your employee.
Responded earlier than expected and quickly resolved the problems
Darlene - Philadelphia, PA
Air conditioning problem solved with a tutorial on how to prevent problem in the future
Schlessinger - Philadelphia, PA
Great innovative repair
Fast service and diagnostic
Cheis - Philadelphia, PA
I got a call from my tenant that the hot water was not working at my rental property. It has been a very busy week leading up to the 4th and I did not have time to get over there myself and figure out what was wrong. Steve diagnosed a bad breaker, saving me time I did not have for a trip over there (worth the diagnostic fee). Price was high ($250) for how easy it is to swap out a breaker, so I'll just handle that on my own. This way I can come over with the part and be in and out in a few minutes.
Great service, friendly workers
Brian - Philadelphia, PA
Dianne - Philadelphia, PA
Courteous, quick, and knowledgeable
Shawn - Philadelphia, PA
Tom was super friendly, knowledgeable, and quick. Great service as usual.
Gretchen - Philadelphia, PA
Justin, Mike, Chen were beyond amazing! I felt so comfortable throughout the entire process. Thank you so much
On time, quick, great service
Brian - Philadelphia, PA
John Franco was the technician that came to my house. He had previously been to my house to perform maintenance on my HVAC system. He was on time, professional and really pleasant to deal with.
Jim - Philadelphia, PA
Excellent service from beginning to end-complete and understandable explanation of the issue, repair or other options, process and price. Top notch.
Installed refrigeration system for ice cream freezer. Summers can take care of all your commercial refrigeration service or installation needs.
Installed central brass faucet and fixed toilet
Checking over a Goodman cooling system
Maintenance on an Aire Ease cooling system
Performed leak check and charged Luxaire AC system.
Preformed maintenance on a Bryant cooling system
Replaced a bad dual capacitor in a Bryant cooling system.
Cleared condensate drain line for a Unico high velocity air conditioner system.
Repaired a York cooling system.
Located a refrigerant leak in a Carrier cooling system.
Replaced compressor on a Lennox air conditioning system. Checked complete operation.
Diagnosing an issue with a Goodman cooling system.
Heat pump install
Repaired a Goodman cooling system
New faucet, bath and shower valve install and snake drain
Performed maintenance on Payne equipment
Installed gerber faucet
Repairing a Gibson cooling system
Preformed maintenance on a Broan cooling system
Diagnosed a failed blower motor on a York package unit. Ordered new motor.
Repaired a commercial refrigeration cooler
Troubleshoot and repair Lennox commercial packaged rooftop unit.
Replaced shower head
Repaired toilet and inspected drain
Yearly maintenance on a Broan cooling system